This image shows states and provinces that experienced power outages. Not all areas within these political boundaries were affected.
|Date||August 14–16, 2003|
|Duration||A few hours, some last 4 days|
|Location||Northeastern United States, Central Canada|
|Cause||Software bug in the alarm system in the control room of FirstEnergy|
The Northeast blackout of 2003 was a widespread power outage throughout parts of the Northeastern and Midwestern United States, and the Canadian province of Ontario on August 14, 2003, beginning just after 4:10 p.m. EDT.
Most places restored power by midnight (within 7 hours), some as early as 6 p.m. on August 14 (within 2 hours).New York subways resumed limited services around 8 p.m. Full power was restored to New York City and Toronto on August 16. At the time, it was the world's second most widespread blackout in history, after the 1999 Southern Brazil blackout. The outage, which was much more widespread than the Northeast blackout of 1965, affected an estimated 10 million people in southern and central Ontario, and 45 million people in eight U.S. states.
The blackout's proximate cause was a software bug in the alarm system at the control room of FirstEnergy, an Akron, Ohio–based company, which rendered operators unaware of the need to redistribute load after overloaded transmission lines drooped into foliage. What should have been a manageable local blackout cascaded into the collapse of the entire Northeast region.
According to the New York Independent System Operator (NYISO) – the ISO responsible for managing the New York state power grid – a 3,500 megawatt power surge (towards Ontario) affected the transmission grid at 4:10:39 p.m. EDT.
For the next 30 minutes, to 4:40 p.m. EDT, outages were reported in parts of Maryland (Baltimore), Michigan (Detroit), Ohio (Cleveland, Akron, Toledo), Ontario (London, Windsor), New Jersey (Newark), and New York (New York City, Westchester, Orange and Rockland counties, Rochester, Syracuse, Binghamton, Albany).
This was followed by outages in other areas initially unaffected, including all of New York City, portions of southern New York state, New Jersey, Vermont, Connecticut, as well as most of the province of Ontario, including Toronto.Eventually, a large, somewhat triangular area bounded by Lansing, Michigan, Sault Ste. Marie, Ontario, the shore of James Bay, Ottawa, New York, and Toledo was left without power.
According to the official analysis of the blackout prepared by the US and Canadian governments, more than 508 generating units at 265 power plants shut down during the outage. In the minutes before the event, the NYISO-managed power system was carrying 28,700 MW of load. At the height of the outage, the load had dropped to 5,716 MW, a loss of 80%.
Essential services remained in operation in some of these areas. In others, backup generation systems failed. Telephone networks generally remained operational, but the increased demand triggered by the blackout left many circuits overloaded. Water systems in several cities lost pressure, forcing boil-water advisories to be put into effect. Cellular service was interrupted as mobile networks were overloaded with the increase in volume of calls. Major cellular network providers lost service until power was restored.[ citation needed ] Television and radio stations remained on the air, with the help of backup generators, although some stations were knocked off the air for periods ranging from several hours to the length of the entire blackout.[ vague ]
It was a hot day (over 31 °C, or 88 °F) in much of the affected region, and the heat played a role in the initial event that triggered the wider power outage. The high ambient temperature increased energy demand, as people across the region turned on fans and air conditioning. This caused the power lines to sag as higher currents heated the lines.
In areas where power remained off after nightfall, the Milky Way and orbiting artificial satellites became visible to the naked eye in metropolitan areas where they cannot ordinarily be seen due to the effects of particulate air and light pollution.
Most of the Amtrak Northeast Corridor service was interrupted, as it relies on electric for its signaling and crossing systems; electrified commuter railways also shut down.Via Rail in Canada was able to continue most of its service. All airports in the affected area closed immediately, so there were no take-offs, and incoming flights had to be diverted to airports with power. U.S. financial markets, which are completely power-dependent, were also shut down. The reliability of the electrical grid was called into question, meaning it was deficient, of less value, and required substantial investment to repair its shortcomings.
Most places restored power by midnight, as early as 6 p.m. on August 14.New York subways resumed limited services around 8 p.m.. . By midnight, Albany, New York and parts of Long Island, New York; three‐quarters of New Jersey; parts of Pennsylvania, Ohio and Michigan; New London County, Connecticut; parts of downtown Toronto, Mississauga, London; portions of western Ottawa including Kanata and south to Kingston; many areas of the Regional Municipality of Niagara in Ontario; and parts of Southwestern Ontario, particularly areas near the Bruce Nuclear Generating Station, lost power for only 4–8 hours.
By the next morning (August 15), some areas of Manhattan regained power around 05:00, Staten Island regained power around 03:00. Half of the affected portions of Ontario regained power by the morning. By early evening of August 15, two airports, Cleveland Hopkins International Airport and Toronto Pearson International Airport, were back in service. By August 16, power was fully restored in New York and Toronto.
Within the area affected, about 200,000 people continued to have power – in the Niagara Peninsula of Ontario; the homes on Gill Crescent in Oakville, Ontario, the easternmost corner of Ontario (centered on Cornwall); and the Buffalo, NY area, excluding southern Erie county, along the shore of Lake Huron via a feeder line to Owen Sound from Bruce Nuclear Generating Station. Three of the four Bruce B units were able to throttle back their output without a complete shutdown, then reconnect to the grid within five hours: the portion of New York state including parts of Albany and north and west of Albany, a small pocket of mid-east Michigan, the Upper Peninsula of Michigan, and small pockets in New Jersey. The unaffected area was protected by transmission circuit devices at the Sir Adam Beck Hydroelectric Generating Stations in Niagara Falls (coincidentally, the starting point of the Northeast blackout of 1965) at a switching station of the hydroelectric power station in Cornwall, as well as central New York state. Philadelphia and the surrounding mid-Atlantic areas were also completely unaffected because PJM disconnected them. [ which? ] in East China Township, Michigan, remained online for about 36 hours, and residents were informed that the plant would have to shut down in order to facilitate the reboot of the whole system. Orrville, Ohio, was able to restore power within an hour disconnecting the local utility from the larger grid and restarting the coal-fired generator.[ citation needed ]The Saint Clair power plant
This section needs additional citations for verification . (August 2020) (Learn how and when to remove this template message)
The load on any power network must be immediately matched by its supply and its ability to transmit that power. Any overload of a power line or generator can cause costly damage, so the affected device is disconnected from the network if an overload is detected.
The electrical resistance of a power line causes it to produce more heat as the current it carries increases. If this heat is not sufficiently dissipated, the metal conductor in the line will expand and lengthen, so that it sags between supporting structures. If the line sags too low, a flash over to nearby objects (such as trees) may occur, causing a transient increase in current. Automatic protective relays detect the excessively high current and quickly disconnect the line, with the load previously carried by the line transferred to other lines. If the other lines do not have enough spare capacity to accommodate the extra current, their overload protection will react as well, causing a cascading failure.
System operators are responsible for ensuring that power supply and loads remain balanced, and for keeping the system within safe operational limits such that no single fault can cause the system to fail. After a failure affecting their system, operators must obtain more power from generators or other regions or "shed load" (meaning to intentionally cut power or reduce voltage to a given area) until they can be sure that the worst remaining possible failure anywhere in the system will not cause a system collapse. In an emergency, they are expected to immediately shed load as required to bring the system into balance.
To assist the operators there are computer systems, with backups, which issue alarms when there are faults in the transmission or generation system. Power flow modeling tools let them analyze the state of their network, predict whether any parts of it may be overloaded, and predict the worst possible failure remaining, so that they can change the distribution of generation or reconfigure the transmission system to prevent a failure should this situation occur. If the computer systems and their backups fail, the operators are required to monitor the grid manually, instead of relying on computer alerts. If they cannot interpret the state of the power grid in such an event, they follow a contingency plan, contacting other plant and grid operators by telephone if necessary. If there is a failure, they are also required to notify adjacent areas which may be affected, so those can predict the possible effects on their own systems.
A joint federal task force was formed by the governments of Canada and the U.S. to oversee the investigation and report directly to Ottawa and Washington. The task force was led by then-Canadian Natural Resource Minister Herb Dhaliwal and U.S. Energy Secretary Spencer Abraham.
In addition to determining the initial cause of the cascading failure, the investigation of the incident also included an examination of the failure of safeguards designed to prevent a repetition of the Northeast blackout of 1965. The North American Electric Reliability Corporation, a joint Canada-U.S. council, is responsible for dealing with these issues.
On November 19, 2003, Abraham said his department would not seek to punish FirstEnergy Corp for its role in the blackout because current U.S. law does not require electric reliability standards. Abraham stated, "The absence of enforceable reliability standards creates a situation in which there are limits in terms of federal level punishment."
In February 2004, the U.S.-Canada Power System Outage Task Force released their final report, placing the causes of the blackout into four groups:
The report states that a generating plant in Eastlake, Ohio, a suburb northeast of Cleveland, went offline amid high electrical demand, putting a strain on high-voltage power lines (located in Walton Hills, Ohio, a southeast suburb of Cleveland) which later went out of service when they came in contact with "overgrown trees". This trip caused load to transfer to other transmission lines, which were not able to bear the load, tripping their breakers. Once these multiple trips occurred, many generators suddenly lost parts of their loads, so they accelerated out of phase with the grid at different rates, and tripped out to prevent damage. The cascading effect that resulted ultimately forced the shutdown of more than 100 power plants.
A software bug known as a race condition existed in General Electric Energy's Unix-based XA/21 energy management system. Once triggered, the bug stalled FirstEnergy's control room alarm system for over an hour. System operators were unaware of the malfunction. The failure deprived them of both audio and visual alerts for important changes in system state.
Unprocessed events queued up after the alarm system failure and the primary server failed within 30 minutes. Then all applications (including the stalled alarm system) were automatically transferred to the backup server, which itself failed at 14:54. The server failures slowed the screen refresh rate of the operators' computer consoles from 1–3 seconds to 59 seconds per screen. The lack of alarms led operators to dismiss a call from American Electric Power about the tripping and reclosure of a 345 kV shared line in northeast Ohio. But by 15:42, after the control room itself lost power, control room operators informed technical support (who were already troubleshooting the issue) of the alarm system problem.
The following is the blackout's sequence of events on August 14, 2003(times in EDT):
|City||Number of people affected|
|New York City and surrounding areas||14,300,000|
|Toronto metropolitan area and surrounding areas||8,300,000|
|Newark, New Jersey, and surrounding areas||6,980,000|
|Detroit and surrounding areas||6,400,000|
|Cleveland and surrounding areas||2,900,000|
|Ottawa||780,000 of 1,120,000*|
|Buffalo, New York, and surrounding areas||1,100,000|
|Rochester, New York||1,050,000|
|Baltimore and surrounding areas||710,000|
|London, Ontario, and surrounding areas||475,000|
|Kitchener-Cambridge-Waterloo, and surrounding areas||415,000|
* Ottawa-Gatineau is a special case in that it is divided by a provincial boundary and the Ontario and Quebec grids are not synchronously connected. Gatineau had power. One[ who? ] may have seen the drastic cutoff of areas still having power when they were crossing the Portage Bridge between Gatineau and Ottawa—the cutoff was at the provincial line (street lights on the bridge were still lit on the Quebec side of the structure).
With the power fluctuations on the grid, power plants automatically went into "safe mode" to prevent damage in the case of an overload. This put much of the nuclear power offline until those plants could be slowly taken out of "safe mode". In the meantime, all available hydro-electric plants (as well as many coal- and oil-fired plants) were brought online, bringing some electrical power to the areas immediately surrounding the plants by the morning of August 15. Homes and businesses both in the affected area and in nearby areas were requested to limit power usage until the grid was back to full power.
Some areas lost water pressure because pumps lacked power. This loss of pressure caused potential contamination of the water supply. Four million customers of the Detroit water system in eight counties were under a boil-water advisory until August 18, four days after the initial outage. One county, Macomb, ordered all 2,300 restaurants closed until they were decontaminated after the advisory was lifted. Twenty people living on the St. Clair River claim to have been sickened after bathing in the river during the blackout. The accidental release of 140 kg (310 lb) of vinyl chloride from a Sarnia, Ontario chemical plant was not revealed until five days later. Cleveland also lost water pressure and instituted a boil water advisory. Cleveland and New York had sewage spills into waterways, requiring beach closures. Newark, New Jersey, and northern cities had major sewage spills into the Passaic and Hackensack rivers, which flow directly to the Atlantic Ocean. Kingston lost power to sewage pumps, causing raw waste to be dumped into the Cataraqui River at the base of the Rideau Canal.
Amtrak's Northeast Corridor railroad service was stopped north of Philadelphia, and all trains running into and out of New York City were shut down, initially including the Long Island Rail Road and the Metro-North Railroad; both were able to establish a bare-bones "all-diesel" service by the next morning. Canada's Via Rail, which serves Toronto and Montreal, had a few service delays before returning to normal the next morning.
Passenger screenings at affected airports ceased. Regional airports were shut down for this reason. In New York, flights were cancelled even after power had been restored to the airports because of difficulties accessing "electronic-ticket" information. Air Canada flights remained grounded on the morning of August 15 due to reliable power not having been restored to its Mississauga control center. It expected to resume operations by midday. This problem affected all Air Canada service and canceled the most heavily traveled flights to Halifax and Vancouver. At Chicago's Midway International Airport, Southwest Airlines employees spent 48 hours dealing with the disorder caused by the blackout's sudden incidence.
Many gas stations were unable to pump fuel due to lack of electricity. In North Bay, Ontario, for instance, a long line of transport trucks was held up, unable to go further west to Manitoba without refueling. In some cities, traffic problems were compounded by motorists who simply drove until their cars ran out of gas on the highway. Gas stations operating in pockets of Burlington, Ontario, that had power were reported to be charging prices up to $3.78 per US gallon (99.9 cents/Litre) when the going rate prior to the blackout was lower than $2.65/gallon (70¢/L). Customers still lined up for hours to pay prices many people considered price gouging. Station operators claimed that they had a limited supply of gasoline and did not know when their tanks would be refilled, prompting the drastic price increases.
Many oil refineries on the East Coast of the United States shut down as a result of the blackout, and were slow to resume gasoline production. As a result, gasoline prices were expected to rise approximately 10 cents/gallon (3¢/L) in the United States. In Canada, gasoline rationing was also considered by the authorities.
Cellular communication devices were disrupted. This was mainly due to the loss of backup power at the cellular sites where generators ran out of fuel. Where cell sites remained up, some cell phones still went out of service as their batteries ran out of charge without a power source to recharge from. Wired telephone lines continued to work, although some systems were overwhelmed by the volume of traffic, and millions of home users had only cordless telephones depending on house current. Most New York and many Ontario radio stations were momentarily knocked off the air before returning with backup power.
Cable television systems were disabled, and in areas that had power restored (and had power to their television sets), cable subscribers could not receive information until power was restored to the cable provider. Those who relied on the Internet were similarly disconnected from their news source for the duration of the blackout, with the exception of dial-up access from laptop computers, which were widely reported to work until the batteries ran out of charge. Information was available by over-the-air TV and radio reception for those who were equipped to receive TV and/or audio in that way.
The blackout affected communications well outside the immediate area of power outage. The New Jersey-based internet operations of Advance Publications were among those knocked out by the blackout. As a result, the internet editions of Advance newspapers as far removed from the blackout area as The Birmingham News , the New Orleans Times-Picayune , and The Oregonian were offline for days.
Amateur radio operators passed emergency communications during the blackout.
Large numbers of factories were closed in the affected area, and others outside the area were forced to close or slow work because of supply problems and the need to conserve energy while the grid was being stabilized. At one point a 7-hour wait developed for trucks crossing the Ambassador Bridge between Detroit and Windsor due to the lack of electronic border check systems. Freeway congestion in affected areas affected the "just in time" (JIT) supply system. Some industries (including the auto industry) did not return to full production until August 22.
This section does not cite any sources . (July 2012) (Learn how and when to remove this template message)
Almost the entirety of the State of New York lost power. Exceptions included Freeport and Rockville Centre on Long Island, which relied on localized power plants; the Capital District, where power dipped briefly (a few areas, such as portions of Latham, New York, did not lose power at all); the southernmost areas of the Southern Tier of Upstate New York, mostly near Waverly, which relied on power from Pennsylvania; the city of Plattsburgh; Starrett City, Brooklyn, which has auxiliary power; most of the city of Buffalo; and pockets of Amherst in the Buffalo area, running off university power. There were also some small pockets of power in the suburbs of Rochester, as a few smaller power companies operating in those areas were able to keep running. The North Shore Towers complex was unaffected by the blackout due to their on-site self-generating power plant. Power was also available at the Kodak Park facility and its surrounding neighborhood in the city. Power was lost at the Oak Hill Country Club in nearby Pittsford, where the 2003 PGA Championship was being played, which caused minor interruptions to the tournament. Also, that evening's Major League Baseball game between the New York Mets and the San Francisco Giants at Shea Stadium was postponed. In New York, all prisons were blacked out and switched to generator power. The two Indian Point nuclear reactors on the Hudson River near Peekskill, the two reactors at Nine Mile Point nuclear plant, the single reactor at Ginna nuclear plant near Rochester, and the FitzPatrick reactor near Oswego all shut down. With three other nuclear plants shut down in Ohio, Michigan, and New Jersey, a total of nine reactors were affected. The governor of New York, George Pataki, declared a state of emergency.
Verizon's emergency generators failed several times, leaving the emergency services number 9-1-1 out of service for several periods of about a quarter-hour each. New York City's 311 information hotline received over 175,000 calls from concerned residents during the weekend. Amateur radio operators attached to New York City ARES provided a backup communications link to emergency shelters and hospitals. Amateur radio repeaters were supplied with emergency power via generators and batteries and remained functional.
Major U.S. networks (CBS, NBC, ABC and Fox) and some cable television channels (HBO, MTV and Nickelodeon), centered in New York City, were unable to broadcast normally, so backup stations and flagship transmitters in Dallas were used for prime-time TV. ABC ran their news broadcasts from Washington, D.C. instead.
Manhattan, including Wall Street and the headquarters of the United Nations, was completely shut down, as were all area airports (with the exception of Newburgh's Stewart International Airport, which had once been a military airbase and had its own generators), and all New York-area rail transportation including the subway, the PATH lines between Manhattan and New Jersey, New Jersey Transit's rail service, Metro-North, and the Long Island Rail Road, though limited railroad service resumed early Friday morning through the use of diesel trains.Hundreds of people were trapped in elevators; by late evening the New York City Fire Department had reportedly confirmed that all stalled elevators in approximately 800 Manhattan high-rise office and apartment buildings had been cleared. More than 600 subway and commuter rail cars were trapped between stations; New York's Metropolitan Transportation Authority and the Port Authority of New York and New Jersey (which operates the PATH lines) reported that all passengers were evacuated without serious injury. PATH resumed subway service on Sixth Avenue by 9:45 PM that evening, system-wide service resumed at 11 PM. By comparison, full service on the New York City Subway system returned gradually from Friday through Saturday morning.
Without traffic lights, gridlock was reported as people in Lower and Midtown Manhattan fled their offices on foot; for hours into the evening the streets, highways, bridges and tunnels were jammed with traffic and pedestrians leaving Manhattan, though many civilians helped direct traffic. The bus journey from Manhattan to Washington, D.C. (which normally takes four hours) took more than eight hours, with reports that it took four hours just to get out of Manhattan. Many people found themselves trapped in elevators at the start of the blackout, requiring urgent response from the FDNY. Mayor Michael Bloomberg advised residents to open their windows, drink plenty of liquids to avoid heat stroke in the heat, and not to forget their pets. Temperatures were 92 °F (33 °C) with high humidity, as New York had just experienced a record-breaking rain spell that had started at the end of July. With cell phone operation mostly stalled by circuit overloads, New Yorkers were lining up 10 deep or more at pay phones as ordinary telephone service remained largely unaffected. Many people found themselves with no phone service at home.
While some commuters were able to find alternate sleeping arrangements, many were left stranded in New York and slept in parks and on the steps of public buildings. While practically all businesses and retail establishments closed down, many bars and pubs reported a brisk business as many New Yorkers took the opportunity to spend the evening "enjoying" the blackout. Tourists' hotel rooms were blacked out except the hallways and most of the restaurants in lobbies gave out free food to guests. Since most perishable items were going to spoil anyway, many restaurants and citizens simply prepared what they could and served it to anyone who wanted it, leading to vast block parties in many New York City neighborhoods. Any ice cream in frozen storage also had to be quickly served to any and all passers by. The Indigo Girls were scheduled to perform that evening at Central Park SummerStage, and the band took the stage as planned to play one of the only shows in the affected area, using generators that had been filled with fuel that morning. Their performance was not a full-length concert, as they needed to end early to allow all attendees to exit Central Park before dark. The venue also had bathrooms, and vendors cooking food on propane grills.
Forty thousand police officers and the entire fire department were called in to maintain order. At least two fatalities were linked to the use of flames to provide light, and many nonfatal fires also resulted from the use of candles. New York City's Office of Emergency Management activated its Emergency Operations Center, from which more than 70 agencies coordinated response efforts, which included delivery of portable light towers to unlit intersections, generators and diesel fuel to hospitals, and a portable steam generator necessary to power air conditioning units at the American Stock Exchange.
Affected areas included most of Hudson, Morris, Essex, Union, Passaic, and Bergen counties, including the major cities of Paterson and Newark, although some sections of Newark and East Orange still had power; also, small sections of certain towns in Essex, Hudson, and Union counties had power. Power was returned first to the urban areas because of concerns of safety and unrest. Counties as far south as Cumberland were affected, where power was restored within an hour. Some towns in Bergen County only momentarily lost power, and had wild oscillations in power line voltage, ranging from about 90 V to 135 V every few minutes for an hour.[ citation needed ]
The day following the blackout, August 15, the New Jersey Turnpike stopped collecting tolls until 9:00 a.m.
The Baltimore-Washington area was not affected other than transportation scheduling.
Parts of New London, Hartford, New Haven, Litchfield, and Fairfield counties, from Greenwich to Danbury and Bridgeport, were affected, although most of the state had power all evening, aside from a few momentary interruptions that caused computers to reboot. Metro-North trains stopped and remained on the tracks for hours, until they could be towed to the nearest station. Generally, most of the state east of Interstate 91, and some places west of I-91, had power during the duration of the blackout, with some of New Haven's eastern suburbs being seen as the easternmost extreme of the effects of the blackout.
A local controversy ensued in the days after the blackout, when the federal government ordered power companies to energize the HVDC Cross Sound Cable between New Haven and Long Island. This cable had been installed, but not activated due to environment and fishery concerns. The Attorney General of Connecticut (and future U.S. Senator), Richard Blumenthal, and the Governor of New York, George Pataki, traded insults over the cable. Connecticut politicians expressed their outrage that the cable was being turned on, since it did not help anyone in Connecticut, as the cable would transport power from Connecticut to Long Island.
A small area of western Massachusetts was affected. In Worcester the event was of sufficient magnitude to reboot some computers, while in Springfield the effect of the event was enough to cause the automatic startup of commercial and industrial backup generation facilities. Some areas were subjected to lower-than-normal voltage (as low as 100 volts AC) and brownouts for periods of up to 24 hours. The Boston area was spared from the blackout.
About 2.3 million households and businesses were affected, including almost all of Metro Detroit, as well as Lansing, Ann Arbor, and surrounding communities in southeast Michigan. The blackout affected three Michigan utilities: Detroit Edison (whose entire system went down), Lansing Board of Water & Light, and a small portion of Consumers Energy's system in the southeastern corner of the state. Word quickly spread to the surrounding areas without power and many flocked to surrounding areas that still had power, resulting in crowded stores, packed restaurants, booked hotels, and long queues for the gas stations in these towns. Locales closest to the affected areas in the northern Detroit suburbs that did not lose power included the areas of Oxford and Holly, communities along M-24 and M-15, and into the Lapeer and Flint/Tri-Cities area.[ citation needed ] The city limits of Brighton and Howell were unaffected as well, as they received electricity from Consumers Energy via the Genoa-Latson 138 kV line which interconnects Detroit Edison and Consumers Energy. Television and radio stations were temporarily knocked off the air and water supplies were disrupted in Detroit due to the failure of electric pumps. Because of the loss of water pressure all water was required to be boiled before use until August 18. Several schools which had planned to begin the school year August 18 were closed until clean water was available.
A Marathon Oil refinery in Melvindale, near Detroit, suffered a small explosion from gas buildup, necessitating an evacuation within one mile (1.6 km) around the plant and the closure of Interstate 75. Officials feared the release of toxic gases. Heavy rains on August 17 coupled with the lack of sewage pumps closed other expressways and prompted urban flood warnings. Untreated sewage flowed into local rivers in Lansing and Metropolitan Detroit as contingency solutions at some sewage treatment plants failed. In the midst of a summer heat wave, Michiganders were deprived of air conditioning. Several people, mostly elderly individuals, had to be treated for symptoms of heat stroke. In the Detroit area, local television stations' news helicopters were told by each station's management to "stay above the cars' headlights" at night, and to not venture into Downtown Detroit (due to the hazard of flying into an unlit skyscraper). During the days immediately after the blackout, many stations were back on the air, with limited resources. (In one case, WXYZ-TV's news anchor was wearing a T-shirt and shorts, as opposed to his normal news suit, and apologized to viewers for the "rather warm conditions" in the station, as they only had one air conditioner and a couple of fans working.) The Downriver communities had to contend with basements flooded with sewage-laden water on the weekend immediately after the blackout, with water and sewage pumps off from a lack of power, much to the general annoyance of residents in the areas. News crews of the areas broadcast notices during their coverages of the blackouts to the Downriver residents, explaining why the pumps had shorted out, as well as to limit water usage. ("Most places have water pressure, some have low pressure...some have none, and some even have negative pressure. That means in the next few hours, people in the downriver communities should expect flooded basements from, so move all your valuables high up and out of the basements," as WDIV-TV warned.) West Michigan, including the communities of Grand Rapids, Muskegon, and Holland were mostly unaffected, although a large portion was within "seconds" of joining the blackout according to local U.S. Representative Fred Upton. Although right across the border from Sault Ste. Marie, Ontario, Sault Ste. Marie, Michigan was unaffected by the outage, as the two cities are not electrically connected.
Over 540,000 homes and businesses were without power. In Cleveland, water service stopped because the city is supplied by electric pumps and backup electricity was available only on a very limited basis and water had to be boiled for several days afterwards. Portions of the cities of Akron, Mansfield, Massillon, Marion, and Ashland were without power. Cleveland declared a curfew on all persons under the age of 18. At Cedar Point amusement park in Sandusky, park employees had to help guests walk down the steps of the 205-foot-tall (62 m) Magnum XL-200 roller coaster, which had stopped on the lift hill due to the blackout. Several other guests had to be helped off rides as a result of the blackout. In Toledo, the Mud Hens baseball team postponed the game scheduled for that night. Some parts of the city were unaffected by the blackout, notably the suburb of Sylvania. Other surrounding cities like Bowling Green only experienced a brief outage.
The area affected by the blackout included all Southern Ontario, except Pelham, Niagara Falls and Fort Erie, from Windsor to Ottawa and all the way to the Quebec border, except for the Cornwall area.Also affected was Northern Ontario, as far north as Attawapiskat and Moosonee on James Bay and west to Marathon on the Lake Superior shoreline. Communities affected in northern Ontario included Timmins, Cochrane, Sudbury, Kirkland Lake, North Bay, Wawa, and Sault Ste. Marie. Most of Northwestern Ontario (including Thunder Bay) was not affected.
Traffic lights, which had no backup power, were all knocked out. All intersections were to be considered an all-way stop. Coupled with the beginning of the evening rush hour, this caused traffic problems. In many major and minor intersections in both large cities, such as Ottawa and Toronto, ordinary citizens began directing traffic until police or others relieved them. Since there were not enough police officers to direct traffic at every intersection during the afternoon rush hour, passing police officers distributed fluorescent jackets to people who were directing traffic. Drivers and pedestrians generally followed the instructions from them even though they were not police officers.
In Ottawa, the federal government was shut down. The Parliamentary Precinct and Parliament Hill were evacuated.
In Toronto, the Toronto subway and RT and the Toronto streetcar system were shut down.Many passengers had to be evacuated from subway trains by walking through the tunnels. Major Toronto hospitals reported that they had switched to generators and did not experience problems. The 9-1-1 system was operational. The streetcars remained suspended on August 18 and 19, resuming after assurances they would be exempt from any potential rotating blackouts. Toronto officials asked residents to curtail unnecessary use of water, as pumps were not working and there was only a 24-hour supply. Entertainment events were canceled for several days. English band Radiohead rescheduled a planned August 16 concert in Toronto until the following October 15 due to the power outage. The opening of the Canadian National Exhibition, scheduled for August 15, was postponed to August 19. The roof of the Skydome in Toronto remained open in an effort to conserve power until August 21, when a thunderstorm struck.
Large disruptions of truck traffic in northeastern Ontario were reported due to the unavailability of fuel, including the backlog near North Bay. The tunnel and bridge between Windsor and Detroit were also closed, with the bridge's pillars illuminated by emergency floodlights, as to not pose a shipping and airplane hazard.
About 140 miners were marooned underground in the Falconbridge mine in Sudbury when the power went out. Mine officials said they were safe and could be evacuated if necessary, but were not, due to the risks of doing so with no power. They were safely evacuated by the morning. In Sarnia, a refinery scrubber lost power and released above-normal levels of pollution; residents were advised to close their windows.
On the evening of August 14, Ontario premier Ernie Eves declared a state of emergency, instructing nonessential personnel not to go to work the next day and that rolling blackouts could occur for weeks.Residents were asked not to use televisions, washing machines, or air conditioners if possible, and warned that some restored power might go off again. Although the full state of emergency was lifted the next day, residents were warned that the normal amount of power would not be available for days, and were still asked to reduce power consumption.
For two days of this recovery period, diversion of water from the Niagara River for hydroelectric generation was increased to the maximum level, normally used only at night and in winter in order to maintain the scenic appearance of Niagara Falls. The resultant drop in the river level below the falls meant that the Maid of the Mist tour boats could not dock safely, and their operation had to be suspended.
The Petro-Canada refinery in Oakville had to perform an emergency shutdown due to the lack of power. The plant's flare system produced large flames during the shutdown, leading to erroneous reports in the media that there had been a fire in the plant.[ citation needed ] The Petro Canada lubricants plant in Mississauga experienced a fire one week later while restarting normal operations.
Many Torontonians remember that night as a moment where the community came together: "Without power, residents of Toronto took to the streets to help direct traffic; florists arranged flowers for weddings by candlelight; and convenience stores served customers in the blackness. The night sky was a rarely seen canopy of dazzling stars, twinkling down on the darkened city through soft summer heat that lingered into the evening."
The blackout was confined to the northwest portion of the state. According to emergency officials in Erie, Crawford, Venango, Clarion, Bradford, Forest and Warren counties, outages lasted into the night, but there were no serious injuries or incidents.
In New York, about 3,000 fire calls were reported, many from people using candles. Emergency services responded to 80,000 calls for help, more than double the average.
From 4 p.m. of August 14 to midnight of August 15, there were 60 all-hands or greater alarm fires, caused mostly by candles. The FDNY answered over 7,500 calls which resulted in the transmission of over 4,000 alarms.
The blackout contributed to almost 100 deaths.
The blackout prompted the federal government of the United States to include reliability provisions in the Energy Policy Act of 2005. The standards of the North American Electric Reliability Corporation became mandatory for U.S. electricity providers.
In the United States, the Bush administration had emphasized the need for changes to the U.S. national energy policy, critical infrastructure protection, and homeland security. During the blackout, most systems that would detect unauthorized border crossings, port landings, or detect unauthorized access to many vulnerable sites failed. There was considerable fear that future blackouts would be exploited for terrorism. In addition, the failure highlighted the ease with which the power grid could be taken down.
The Ontario government fell in a provincial election held in October 2003; power had long been a major issue. The government may have been hurt by the success of Quebec and Manitoba, which were not affected whereas Ontario was shut down. The extra publicity given to Ontario's need to import electricity from the United States, mostly due to a decision of the government not to expand the province's power generating capabilities, may also have adversely affected the Conservative government. Premier Ernie Eves's handling of the crisis was also criticized; he was not heard from until long after Mayor Bloomberg and Governor Pataki had spoken out. Due to the regular announcements he gave in the days following the blackout, Eves enjoyed a moderate increase in the polls that his party took as a sign of an opportunity to call an election they could win, but they lost instead.
By evening of August 14, power had been restored to:
Con Edison retracted its claim that New York City would have power by 1 a.m. That night some areas of Manhattan regained power at approximately 5 a.m. (August 15), the New York City borough of Staten Island regained power around 3 a.m. on August 15, and Niagara Mohawk predicted that the Niagara Falls area would have to wait until 8 a.m. In the New York City borough of Brooklyn power was not fully restored until around sunset on August 15.
By early evening of August 15, two airports, Cleveland Hopkins International Airport and Toronto Pearson International Airport, were back in service.
Half of the affected part of Ontario had power by the morning of August 15, though even in areas where it had come back online, some services were still disrupted or running at lower levels. The last areas to regain power were usually suffering from trouble at local electrical substations that was not directly related to the blackout itself.
By August 16, power was fully restored in New York and Toronto. Toronto's subway and streetcars remained out of service until August 18 to prevent the possibility of equipment being stuck in awkward locations if the power was interrupted again. Power had been mostly restored in Ottawa, though authorities warned of possible additional disruptions and advised conservation as power continued to be restored to other areas. Ontarians were asked to reduce their electricity use by 50% until all generating stations could be brought back on line. Four remained out of service on the 19th. Illuminated billboards were largely dormant for the week following the blackout, and many stores had only a portion of their lights on.
Preparations against the possible disruptions threatened by the Year 2000 problem have been credited for the installation of new electrical equipment and systems which allowed for a relatively rapid restoration of power in some areas.[ citation needed ]
In the United States and Canada, the regional blackout dominated news broadcasts and news headlines beginning August 15. U.S. and Canadian television networks pre-empted normal programming in favor of full-time, advertising-free coverage of the unfolding story. Once terrorism had been conclusively ruled out as a cause, many stations switched back to normal programming following an 8:30 p.m. EDT address by President George W. Bush. National news stations, such as the CBC and CNN, continued to cover the story by inviting politicians and electrical experts to discuss the situation and suggest ways to prevent blackouts. Internationally, coverage of the story focused on the development of the situation in the New York City metropolitan area.[ citation needed ]
This section needs additional citations for verification . (May 2007) (Learn how and when to remove this template message)
During the first two hours of the event, various officials offered speculative explanations as to its root cause:
In Ontario, some cities took part in power conservation challenges or events to remind citizens of the blackout, the most well-known event being the Voluntary Blackout Day hosted by the Ontario Power Authority (OPA). During these events, citizens were encouraged to maximize their energy conservation activities. Smaller cities such as London, Guelph, Woodstock and Waterloo took part in the challenges annually. The final Voluntary Blackout Day was held on August 14, 2010 with OPA moving to more year-round energy conservation efforts.
A power outage is the loss of the electrical power network supply to an end user.
The northeast blackout of 1965 was a significant disruption in the supply of electricity on Tuesday, November 9, 1965, affecting parts of Ontario in Canada and Connecticut, Massachusetts, New Hampshire, New Jersey, New York, Rhode Island, Pennsylvania, and Vermont in the United States. Over 30 million people and 80,000 square miles (207,000 km2) were left without electricity for up to 13 hours.
The 2003 London blackout was a serious power outage that occurred in parts of southern London and north-west Kent on 28 August 2003. It was the largest blackout in South East England since the Great Storm of 1987, affecting an estimated 500,000 people.
The New York City blackout of 1977 was an electricity blackout that affected most of New York City on July 13–14, 1977. The only neighborhoods in the city that were not affected were in southern Queens, which were part of the Long Island Lighting Company system, as well as the Pratt Institute campus in Brooklyn, as well as some other large apartment and commercial complexes that operated their own historic power generators.
In the electricity sector in the United Kingdom the National Grid is the high-voltage electric power transmission network serving Great Britain, connecting power stations and major substations and ensuring that electricity generated anywhere on it can be used to satisfy demand elsewhere. The network covers the great majority of Great Britain and several of the surrounding islands. It does not cover Ireland; Northern Ireland is part of a single electricity market with the Republic of Ireland.
The 2003 Italy blackout was a serious power outage that affected all of the Italian Peninsula for 12 hours and part of Switzerland near Geneva for 3 hours on 28 September 2003. It was the largest blackout in the series of blackouts in 2003, involving about 56 million people.
An electrical grid, electric grid or power grid, is an interconnected network for delivering electricity from producers to consumers. It consists of:
The 1999 Southern Brazil blackout was a widespread power outage that occurred in Brazil on March 11 to June 22, 1999.
The 1996 Western North America blackouts were two widespread power outages that occurred across Western Canada, the Western United States, and Northwest Mexico on July 2 and August 10, 1996. They were spread 6 weeks apart and were thought to be similarly caused by excess demand during a hot summer.
The 2010 Chile blackout was an electric power outage that affected most of Chile on March 14, 2010. It began at 8:44 pm on Sunday and continued into the next day. The power was restored in a few hours in some areas, and by midnight in most areas, except in the Biobío Region.
The 2011 Southwest blackout, sometimes referred to as the Great Blackout of 2011, was a widespread power outage that affected the San Diego–Tijuana area, southern Orange County, the Imperial Valley, Mexicali Valley, and Coachella Valley, and parts of Arizona. It occurred on Thursday, September 8, 2011, beginning at about 3:38 pm PDT. It was the largest power failure in California history.
Several major power outages have occurred in the country of Malaysia.
Two severe power blackouts affected most of northern and eastern India on 30 and 31 July 2012. The 30 July 2012 blackout affected over 400 million people and was briefly the largest power outage in history by number of people affected, beating the January 2001 blackout in Northern India. The blackout on 31 July is the largest power outage in history. The outage affected more than 620 million people, about 9% of the world population, or half of India's population, spread across 22 states in Northern, Eastern, and Northeast India. An estimated 32 gigawatts of generating capacity was taken offline. Of the affected population, 320 million initially had power, while the rest lacked direct access. Electric service was restored in the affected locations between 31 July and 1 August 2012.
The Maanshan Nuclear Power Plant is a nuclear power plant located near South Bay, Hengchun, Pingtung County, Taiwan. The plant is Taiwan's third nuclear power plant and second-largest in generation capacity. The expected lifespan of this plant is 60 years.
The December 2013 North American storm complex was a significant storm complex that had all sorts of severe weather, including a winter storm, a crippling ice storm and a tornado outbreak that impacted the central and eastern portions of Canada, parts of the Central Great Plains, the Southern United States, and the northeastern United States from 20 to 23 December 2013. Formed in the South Central United States, the storm headed across the Great Plains towards Canada into Atlantic Canada and northeastern United States where the storm dissipated on 23 December 2013. The storm produced freezing rain and snow to the affected areas which caused massive damage to electric power transmission and trees. The storm resulted in 27 deaths, loss of power to over a million residents and over $200 million in damages. The storm produced similar conditions to the ice storm of 1998 which affected similar areas.
The South Australian blackout of 2016 was a widespread power outage in South Australia that occurred as a result of storm damage to electricity transmission infrastructure on 28 September 2016. The cascading failure of the electricity transmission network resulted in almost the entire state losing its electricity supply, affecting 850,000 SA customers. Kangaroo Island did not lose its supply, as the Kangaroo Island power station had been built to supply the island for the contingency of a failure in the power cable under the Backstairs Passage.
Nationwide recurring electrical blackouts in Venezuela began in March 2019. Experts and state-run Corpoelec sources attribute the electricity shortages to lack of maintenance and to a lack of technical expertise in the country resulting from a brain drain; Nicolás Maduro's administration attributes them to sabotage. Since March, various nationwide blackouts occurred in the country.
On 16 June 2019, a large-scale power outage struck most of Argentina, all of Uruguay, and parts of Paraguay, leaving an estimated total of 48 million people without electrical supply.
The West Side of Manhattan in New York City experienced a power failure on July 13, 2019, at approximately 7 p.m. EDT. Con Edison is the energy utility serving the area, and they reported that approximately 73,000 customers were without power. Power was fully restored by midnight. The power failure occurred on the 42nd anniversary of the New York City blackout of 1977, which left nine million customers without power.